On Sun, 31 Mar 2013 17:17:16 -0700 (PDT), " email@example.com"
its like a heat pump and I think it was at least partially under the ocean or
bay or whatever during the hurricane "Sandy". It sits about a foot off the
ground and I wonder if it can be salvaged with just a circuit board replacement
and maybe a blower motor.
Take a close look. How much corrosion is on the coils? All the
wiring might need to be replaced, salt water inside the insulation is
not a good thing.
They do make "Shore Duty" rated condensers at about $200-300 more than
standard. If you put in a standard unit you will see lots of
corrsion on all the coils in just a few years.
Mount it 3 feet off the ground. At least that worked for Ocean City
Remove 333 to reply.