So I posted a thread a while back about my new circuit I installed.
I originally ran 12-2 wire for a 15 amp breaker w/ 15amp GFI in a garage. The
circuit was connected to a single receptacle and single tool (planer).
Well, my planer is still tripping the breaker on 'first turn on'. If I reset
the tool would start w/ no tripping.
Today I replaced the 15A w/ 20A breaker and replaced 15A GFI w/ 20 Amp GFI. It
looks like the problem is fixed.
Who ever it was that suggested I use 20A instead of 15A you were correct and I
was wrong. I should have went w/ 20 amp originally as suggested.