I know we discuss it here very often.. but now I need a refresher..
Working on a well system for a submersible pump. Had a bad gauge on
it and was at times not wanting to cut off at high pressure...
I replaced the gauge, and cut in / out switch. and pre loaded air
charge in bladder tank.. per tank instructions ie: "with no pressure
or water in bottom of tank, air pressure in bladder should be 2 lbs
less than cut in pressure of switch"
The switch is in at 40, cut out at 60..
Shouldn't this switch /relay be closed when it's sitting on the
shelf.. it being less than 40 psi?
I want to think I've got a bad switch.. it's a Lowes made in china..
Won't be going back there (the old home place) till Sunday.. Any ideas
Chuck (in SC)
Well, if it's truly a switch AND relay, the switch WILL be closed, but
the relay WON'T since it needs voltage to energize its coil (Said
voltage being controlled by the switch.) and there's no voltage supplied
to it when it's "on the shelf".
Sounds like it should be. Are you sure that you have the correct
terminals (there may be both NO and NC terminals).
The ones that am am familiar with have a cover that you can
take off and see the contacts.
On Fri, 20 Jul 2007 23:10:35 -0400, "Chuck (in SC)" <> wrote:
Some of these also have a low pressure cut-out to prevent the pump
running dry. Is there a lever on the side of the switch housing? If
so, you have to use the lever to mechanically actuate the contacts
long enough to build up the minimum pressure before the automatic
action will take over. Once the pressure builds over 5 PSI or so, you
release the lever and the switch will work as you would expect.
It's been years since I had helped my dad work on this system.. and I
remember that this may be the issue.. the 5 psi,, cocks the relay you
Also.. the Square D brand relay (that I replaced) had two
adjustments, one for low and one for high setting.. the new one.. has
just one adjustment for cut in, and cut out is estimated to be 20 lbs
higher than that....
Thanks for info..
Still have 20 hours before I have to head back there to do more work..
and hope to get it working right..
Chuck (in SC)
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.