traced to problem to a high resistance connection in the splice on one
hot side at the transformer.
It had been there since the transformer was installed in 1981. Just
gotten worse over the years. The previous owner fought problems with the
heat pump and well pump for years.
The lineman replaced the splice crimp connector and everything checks
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.