I had the same problem and I suspected low vacuum pressure took so I took out
the blower and found out that air was leaking around the gasket. I removed some
of the spacers from under the fan and tightened it down and the vacuum switch
functions normally now.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.