Low voltage on switch

I have low voltage (~82v) on a light switch in the kitchen. I'm assuming this is why the light bulb doesn't go on. What is the likely solution (other switches on the same circuit read normally ~120v. Thanks.
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

Is the 82 volts the drop across the swithc when turned off or the drop across the bulb when the switch is on?........Good Luck, Ross
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

The switch is turned off. Thanks.
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

Measure the voltage across the switch with it turned on....if there is no drop the switch is probably not the problem...And how is the connection in the socket. Remove the bulb, turn on the switch and measure the voltage in the socket...if it is good, you might have a bad connection with the bulb/bad socket. I have also seen cheap bulbs that won't make a good connection with any socket...I like Phillips....good luck John..........Ross
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
I think you may be reading in series with the light. Put your tester leads the hot screw of the switch and ground and see what you read. It seems like you may just have a bad switch

<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
John1 wrote:

Keep in mind that if you are not reading from hot to neutral with power to the switch and you are using a new digital type meter, you may be getting false readings due to the very high internal resistance of the meter. You also want to make sure you are not reading voltage with the lamp in the circuit.
--
Joseph Meehan

26 + 6 = 1 It's Irish Math
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

Neutral in the switch box (I assume you're measuring hot-to-neutral) might be floating. That can give all kinds of funky readings, depending on the load.
If you know where the feed for this box is coming from, check the connections at the next upstream box.
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

Did it ever work correctly? If so, its likely the switch. Try a new one.
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

Site Timeline

• Tough electrical problem!

• - next thread in Home Repair
• Chilly house after renovation.

• - previous thread in Home Repair

• Common property door lock keeps getting changed by one of the unit owners

• - last updated thread in Home Repair
• Common property door lock keeps getting changed by one of the unit owners

• - the site's last updated thread. Posted in Home Repair
• Share To

HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here. All logos and trade names are the property of their respective owners.