I will do this. Is this a legal way to wire it this way? (Where the outlet
looses power if the light bulb is removed?)
On Monday, March 25, 2013 7:34:48 AM UTC-5, firstname.lastname@example.org wrote:
fan,light and one for the vanity light. Each switch has a white wire, a bla
ck wire, and a ground. When checking with a voltmeter, the white wire on bo
th switches always has power. Each black wire only has power when the switc
h is turned on. I am assuming the white wire is the power wire. Can I take
these white wires off the switches, connect them to the top and bottom "hot
" terminal on the gfi outlet, then feed the switches from both terminals on
the other side of the gfi? When I did this messing around with the switche
s, everything worked properly. I just thought that the black wire was alway
s the constant power wire.
On 03/25/2013 02:49 PM, email@example.com wrote:
Short answer, no.
Long answer, no, because you have no idea what the voltage across any
load plugged into the recep will be because of the light bulb(s) in
series with the neutral, which will drop the voltage some amount below
nominal, that amount being dependent on the load connected to the recep
and the wattage/resistance of the light bulb. A recep should always
have full 120V at all times, that is, the wires go straight to the
breaker or fuse box with no interruptions (other than splices.)
There are times when you might want to use a light bulb in series with a
load (e.g. powering up an old tube radio for the first time) but
residential wiring is not one of them.
As I said in a previous post, "doing it right" is likely going to
involve a 12/2 homerun to the panel and a new 20A breaker.
replace "roosters" with "cox" to reply.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.