My Linde Nitrogen purging regulator doesn't regulate pressure to well
below about 25 PSI. Other then buying a low flow setup how do you all
keep a very low Nitrogen purge flowing while brazing linesets.
If you dry fit all the lineset connections and give it a good Nitrogen
purge and then shut off the flow will the residual Nitrogen keep the
Oxygen from invading. Nitrogen is only one notch lighter then Oxygen
so I don't think it's going to get too anxious to escape.
when you fit up the copper, wrap each joint with one wrap of
electrical tape, being careful not to get the tape hot enuf to melt if
welding nearby. peel the tape before welding the joint
then crank the nitro reg down to its lowest point possible and still
get a flow. if i need finer control, i'll run it thru the low side on
my guage set and then crank it down to 1 psi or less.
small piece of quarter inch copper onto one end. Next, put a quarter inch flare
nut on the end, use a flare union and your refrigeration gauge set, hook your
gauge set to your nitrogen regulator and there you go with you .5 to 1 PSI
Hey, that's a great idea!! I was thinking of ways of restriction but I
didn't want to have a situation where high excessive pressure would blow out
or expand my hoses, this prevents this from happening since the regulator
itself has a relief, but we all know that it could release after we expand
the hoses. What diameter cap tube in your experience would you say works
well? Man, I like this idea......
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.