If an attic fan is properly sized, and properly installed, what should be
the temperature differential between the outside air temperature and the
attic temperature, while the fan is running?
Assume there is plentiful air intake in the attic from outside air.
After your last post what makes you think.......?
"I have been called bad before. Many have said I do things that are not
correct to do. I don't believe in talk such as this. I am nice man, with
happy feelings. All of the time. First, a joke. What do you get when you
cross an owl with a bungee cord?
[pause] My ass. Nyah, haha, haha, haha, ENOUGH!"
Attic temperature depends on the amount of solar radiation, construction
details and the rate of ventilation. Calculations indicate that on a July
day in Texas, a ventilation rate of one air change per minute for a typical
attic using 95-degree F air will lower the peak attic temperature to about
101 degrees F. Providing half air change per minute will lower the
temperature to about 106 degrees F. Thus, the first half change per minute
is most effective and a doubling of this rate only achieves about 5 degrees
F additional cooling. Studies indicate that further increases in ventilation
are not effective in significantly reducing attic temperatures.
Calculate the required summer ventilation rate by determining the volume of
attic space and dividing by 2. This will be the cfm (cubic feet per minute)
of ventilation air needed. The volume is determined approximately for a
rectangular house by multiplying the height from the ceiling to the
peak/ridge (H) times the width of the house (W) times the length (L) and
dividing by 2 -- ( H x W x L / 2 ). For a gable roof, this will be
reasonably accurate. For a hip roof house, the volume will be overestimated
"W" < email@example.com> wrote in message
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.