The subject nearly says it:
I have a Worcester Combi 28CDi. I top up to 1.5bar.
I guess there is no hard and fast answer - but typically how often
should I have to top up; how often should I have to bleed the highest
radiator (a fair amount of gas/air collects in it).
As a matter of interest - in a sealed system how does the air/gas get
in to require bleeding - I am having to do it often - does this imply
a leak - water out/air in or does the air/gas come out of the water?
In article ,
Julian Grant writes:
On a newly installed system (6 years ago), I top up about once
every 18 months when it drops from 1 bar to 0.75 bar (cold).
The system isn't ever completely sealed -- valve and diverter
shafts for example couldn't be turned if they were completely
A small leak, contrary to what you might think actually lets air
in to a pressurised system. Air is much less viscous than water
and will pass through a leak much faster. Due to the temperature
cycling of the water in the system and the consequent change in
soluability and partial pressure of Oxygen and Nitrogen in the
water, an air molecule just next to a leak will often see the
not-quite-sealed heating system as a partial vacuum, even though
the water is still under pressure, so the air is sucked in to
dissolve in the water. When the system heats up, the solubility
reduces forcing some of the dissolved air to turn back into gas
and form bubbles, which then collect at high points. Oxygen in
the water can also cause rusting of metalwork, which releases
hydrogen, which can also collect in the high points. Inhibitors
prevent this reaction, but are steadily used in doing so (and
may also be lost by leaks and topping up dilution).
On 05 Jan 2008 14:01:21 GMT, email@example.com (Andrew
Thanks - as I have said above I will try a bag on the outlet pipe to
see if I am losing any there - I will also monitor accurate refill
On Sat, 05 Jan 2008 11:48:38 +0000, Julian Grant
Many thanks to all previous responders and the FAQ:
Indeed, the plastic bag over the discharge pipe shows that there is a
very steady drip from it.
I will open the release a couple of times to see if it clears it -
other than that I will consider whether to get the valve replaced.