We recently moved to a 70s house, where from the survey, and my inspection
pre sale, the electrical installation was in pretty good nick, if somewhat
limited in numbers of sockets.
Having now spent the last few months crawling around the innards of the
house I now have a much more comprehensive understanding of the electrical
installation, and one item that initially worried me was that the power
cables, and some of the lighting cables, are in PVC insulated copper coated
aluminium cable. However, despite the well documented problems in the US
with plain aluminium cable, this Cu/Al cable seems OK. The PCV is flexible,
showing no sign of cracking or leaching, and the copper wire surface is
bright, and showing no sign of adhering to the PVC. I've now replaced about
half of the rather tatty 13A sockets, and most of the light switches, and
none of the connections were showing signs of creep, oxidation, heating, and
other nasties, which accords with the comment in
http://wiki.diyfaq.org.uk/index.php?title=Historic_Mains_Cables re this type
The ring cable has seven strands for phase and neutral, with an overall
diameter of 2.3mm, and a single strand CPC of 1.3mm diameter, which in terms
of its performance looks to me like a composite of imperial copper 7/029
equivalent for phase/neutral, and the equivalent of 1mm metric copper CPC.
Lighting cable has three strands at 1.4mm overall, and a 1mm CPC. Given that
the rings are on the RCD side of the CU, and are fed via 30A MCBs, it seems
to me that the cable can continue in service where necessary (with
I can't find any information on the current capacity and performance of
Cu/Al cables - does anyone have any thoughts or info here, as to whether my
assumptions as to their continued use are correct? The cables are marked
"Enfield-Standard Johnson and Phillips 600/1000V Copperclad" incidentally.
Which brings me on to my second query. I now need to join a number of
cables, and to do it neatly in a comparatively small space. The obvious
solution is to use crimps, and the seven stranded cables will just go neatly
into blue crimps. I would, of course, use a decent ratchet crimp tool. Given
all the above a properly made crimped joint looks as though it should be
fine, but wondered if the team has any experience here?
One last comment - the wiki section on crimping
http://wiki.diyfaq.org.uk/index.php?title Êble_crimping all looks very
sensible and well laid out. I have one query though - the photos show three
blue crimps for 2.5mm T&E, which looks right for phase and neutral, but I
would have thought a red crimp (despite the unfortunate colour) would be
better for the CPC. I would assume that crimps work best if matched fairly
well in size to the conductor concerned?
Thanks for your thoughts and comments,