I have to replace the secondary heat exchanger again in My heatline
S30 boiler again!!. Does anybody know if I need to drain the system
down or do I just need to turn off the water supply. It would seem to
me that the the divertor valves mean I should get away with just
turning off the mains water, or am I missing something
Thanks in advance
On Feb 28, 12:40 pm, email@example.com wrote:
Hi, when I remove mine (an Ariston) I need to turn off the incoming
mains water (which goes through the secondary water circuit) and also
isolate the flow and return through the primary circuit, which is just
a matter of a quarter turn of the relevant valves going into the
boiler. Incidentally, before I do isolate flow and return I drain a
couple of pints of water from the system so that it's not under
pressure, otherwise you'll get a sudden burst of water when you remove
Do you really need to replace it? Unless it's leaking or damaged in
some way you can usually restore it to full functionality by descaling
and generally flushing the crap out.
Thanks, Have descaled it a couple of times now, had it 9 years, and
wondered if its time to replace this time?
Does anybody think its worth trying and clean the rads out by flushing
the system with fresh water, as power flush seems very expensive!
It's expected to scale up from time to time in hard water area.
It's not generally expected to fail. If the primary side becomes
blocked with rust flaking away from the insides of the radiators,
that can be hard to clear out. Hard water scale on the secondary
side should be easy, but don't underestimate the ammount a heat
exchanger can hold, and you will need a lot of descaling chemical.
I'd suggest buying a tub of Furnox DS-3, which is designed for this.
It's Sulphamic acid, combined with an indicator dye so you can tell
when the solution is used up and needs replacing, and a perfume so
you don't accidently drink it.
Only if you have some reason to believe it needs doing.
A properly maintained system shouldn't corrode and leave debris
in the radiators. If radiators are cold at mid-bottom and both
pipes are hot, then that indicates a pile of sludge in the
[email address is not usable -- followup in the newsgroup]
On Feb 28, 4:33 pm, firstname.lastname@example.org (Andrew Gabriel)
I have noticed radiators at the top of the house which are a cheap
variety when bleed produce blackish water and on one double panel rad
the rear panel does not heat and if bled produces nothing, air or
water, though as far as I remember its always been cold on rear panel
The downstairs expensive Delonghi ones produce nice clear water, not
sure if that helps.
Thanks for your advice.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.