Trying to sort out the design of my new CH and am tring to find out
what the effect of pipe length is on flow and output, so i can work
out what size pipes i will require to put in. I have calculated all
the radiator sizes so this really is the last thing i need to work
find out before I can start.
Thanks for your help.
If the flow and return are any more than 12 mtrs in length, then they have
to be insulated 28 mm. Anything under that length can be insulated 22 mm.
The insulation is the important part as it stops you losing the heat in the
parts you don't want to.
Outgoing mail is certified Virus Free.
On 31 Jul 2003 06:51:27 -0700, email@example.com (Peter Charlwood)
Broadly, to avoid excessive noise, the flow rate should be kept at
The radiator outputs, which you need to correct for operating
temperature, allow you to calculate the flow rate (mass x specific
heat x temperature rise).
As you then group the radiators together into trunk pipes the figures
are added and you then need to account for the total flow of those
The Copper Development Association has a useful article for working it
all out fairly easily.
Download articles P150 and TN39
If you wanted to be really scientific you can use the graphs of flow
data, but it isn't necessary. Article P150 has a simple to use
method to work everything out using tables of numbers. A little work
with a calculator and you're done.
Typically you will find that you may need 28mm close to the boiler or
for long runs, although usually 22mm is enough, then 15rmm for most
other requirements being careful not to aggregate too much load onto
15mm lengths. If you want to then go for 8 or 10mm microbore you can
use the same method to calculate that.
To email, substitute .nospam with .gl
On Thu, 31 Jul 2003 16:34:56 +0100, in uk.d-i-y Andy Hall
I once extracted a formula to relate flow velocity, pipe
resistance and bore:
R = y * (V ^ x)
where R = Resistance in inches of water per 100 foot pipe run
V = Flow rate in pounds per hour
x and y vary for different pipe sizes
Size(mm) x y
8 1.7650 1.225 *10^-2
10 1.7430 4.150 *10^-3
15 1.7180 5.836 *10^-4
22 1.7495 7.070 *10^-5
28 1.8913 6.648 *10^-6
(Table looks better in fixed point font)
For 8mm tube this is for 0.6mm wall thickness, for 10mm it is 0.7mm
These are empirical formula that I derived from tables. If anyone has an
analytic version or a single formula that takes bore into account I
would like to have it.
From this a 22mm pipe has about 1/7th the resistance of a 15mm pipe of
the same length and flow rate. A 28mm pipe has about 1/30th the
resistance of 15mm.
The uk.d-i-y FAQ is at http://www.diyfaq.org.uk /
Replace NO DOT SPAM with BIGFOOT DOT COM to reply
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.