I found my pilot light out on my furnace recently and the thermocouple
looked like it was perhaps the same age as the furnace
(~15yrs). Relighting attempts failed. The furnace had been serviced
recently due a home sale, and I'd hate to have an $80 service call for
an $8 part.
So, off to the hardware store, standard 24V 48" thermocouple purchased
(longer than the one it replaced), got it into the furnace and
... pilot still won't stay lit after being manually lighted. I
manually kept it going for over a minute on each of several attempts
only to watch the pilot go out after releasing the button.
Now, the thermocouple doesn't appear to sit directly in the flame on
this model, but mighty close. Without bending the actual thermocouple
since the tc and pilot are in fixed positions in the bracket, the way
the pilot burns doesn't seem to hit the tc directly. The old
thermocouple wasn't bent either.
Any clues or thoughts other than "call for service" (which of course
would be the next step.).
Should the tc be bent into the flame or does that ruin them?
Thanks for any help!
The tip (approximately 3/8 of an inch) MUST be submerged into the flame.
The thermocouple must not be bent at all!
Your furnace has safely not allowed you to light the pilot by design. A
minimum pilot must be established to safely light the main burner/s. The
distance between the pilot burner and thermocouple ensures the flame is
large enough. The placement of the pilot assembly onto the main burner, as
well as the flame pattern of the pilot is engineered into the manufacturers
design for a dependable and safe system. If the pilot flame was not large
enough or mounted in the wrong position to light the main burner
immediately, a delayed ignition (read BOOM) will occur.
The pilot assembly may be dirty, or the fuel tube to the pilot may be
leaking gas, or a good size list of other possibilities are causing the
pilot flame to be inadequate.
If it was only the thermocouple, you would be OK with replacing it.
However, your attempt to correct this problem, to get the burner to start,
may leave your furnace in a very unsafe state. No one over the internet can
say "Yah, everything looks good ". :-)
Ask around for a better recommendation if you did not feel good about the
last service company. Good luck.
Good to know! It is old and that wouldn't be its only issue.
If I wanted to test the old thermocouple by holding it in, say the
flame of the gas range burner, could a digital multimeter be used to
see if the old one was even bad?
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.