On Tue, 14 Oct 2008 12:15:03 -0700 (PDT), DerbyDad03
Maybe it's caused by the pressure reducing valve itself. What seems
strange to me is that you continue to hear water flowing after you
turn off a water valve. Almost like that pressure reducing valve is
not letting enough water in to even keep all the pipes pressurized.
are you getting good flow?
check the washing machine
check the dishawasher
check all faucets where there may be connection from the hot to the
do you have an expansion tank or a pipe filled with air someplace in
the system? sounds like you get a nice oscillation set up, that
might happen if there was air trapped someplace in the system..
although air traps are sometimes installed for the very purpose of
prevenintg water hammer,,,but I could see the air being compressed and
acting like a spring setting up an oscillation
please do come back and tell us after you figure it out.
Just an update...
I was home alone this weekend and tried this:
- Saturday night, I closed the main shutoff.
- I opened every faucet, outside hose bibs, flushed the toilets and
turned on the washer.
- I let the system drain for at least 30 minutes.
- I closed all faucets and bibs, including the toilet shutoffs, turned
off the washer.
- I turned on the main shutoff.
- I went to the farthest fixture and turned it on, waiting for the
hissing and spitting to stop.
- I did the same for all fixtures and bibs, working my way back to the
- I opened the toilet shutoffs.
- I tested a few fixtures - No noise from pipes.
- I spent all day Sunday using various fixtures, took a shower, did
some dishes, washed a car, did some laundry - No noise from pipes.
- Family came home Sunday night. They did some laundry, took some
showers, did some dishes - Bang Bang Bang Bang - Noise was back.
It's not my plumbing...it's my d*mn family! I guess I'll have to send
them away permanently.
I believe I have solved the porblem.
I bought a $13 gauge and checked the pressure before and after my
pressure regulator. It was pushing 85 PSI in both locations, telling
me that my regulator wasn't doing squat.
I replaced the pressure regulator and now read 50 PSI inside the
house. It's been over 24 hours with no banging. Previous excursions
into draining the plumbing would eliminate the banging for just a few
hours, so I am hoping that this time it's gone for good.
The biggest pain now is due to the fact that I had to cut into the
drywall ceiling in my basement bathroom to expose the regulator. Now I
have a big hole to patch - flat taping in a small space - the worst
kind to try and hide!
And yes, I considered moving the regulator to a more accessible spot,
but that would involved some serious modifications to the existing
plumbing for something I hope not to replace for another 30 years, if
On Mon, 27 Oct 2008 08:55:31 -0700 (PDT), DerbyDad03
When you can't match - contrast. Rather than trying to get that
ceiling looking perfect again, why not install a nice little access
door? If you are not that skilled, you can buy ready made access doors
complete with frame, that fit into a precut hole.
I'd like to think I'm skilled enough to trim out an access panel - even
considered doing it. The problem is that the location would make it
difficult to "contrast" it and make it look good at the same time. It's
right near the door on one side, the fan/heater on another side - but
offset a bit, not centered in the room, etc, etc. I think it would stand
out even more than it should, but I'll keep it in mind.
I'm in no hurry to start mudding, so maybe a different solution will
present itself in the meantime.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.