so replace them as they go bad
plus arc fault breakers for
you can install GFCI without a service upgrade
plus the panel is mazed out.
unless expansion is warranted, being maxed out isn't a problem --
it just means you're using all the capacity you initially paid for
I seriously doubt the amount spent will be recovered in a sale
be specific -- what does an upgrade allow that you couldn't do
The e-mail address in our reply-to line is reversed in an attempt to
minimize spam. Our true address is of the form email@example.com.
You know electric service is similiar to a appliance... What other
appliances do you use forever? Its all well and good to save money but
its smart money to invest in your home. upgrading does just that and
trust me a 35 year old maxed out panel will be flagged by a home
inspector as needing upgrading..
tom the great, no doubt you drive a 40 year old car and never replace
anything at your home or you wouldnt ask this........ you old 40 year
old mower is still cutting grass fine?
theres a time for patch and make do, and if you pown a home upgrading
should be a ongoing operation so your entire home doesnt need done at
The problem is the lights dim for a second when the AC and heat come on. My
microwave takes so much power it also dims the lights when it is on. My
current plan is to get a volt and amp meter and hook it to the mains supply
and watch the values when the AC comes on. If the voltage drops then I am
told that the problem is the transformer located 120 feet from my meter.
The transformer is unable to supply sufficient voltage. If the volts and
amps don't drop (or drop very little) then the problem is something else.
You have the right plan there. Jason. But just be damn careful if you
really intend to "hook" an ammeter to the mains supply.
If there's enough "slack" in the mains feed coming into the panel to get
a "clamp on" ammeter around each wire, one at a time, you could do it.
But if there isn't, I wouldn't recommend trying to mess with those input
wires, you probably can't kill the power on them without having the
electric company come and "pull" the meter for you.
Actually, measuring the current isn't really the issue, if the current
peaked too high the main breaker would prolly pop. It's the voltage you
should be monitoring when you kick the AC and heat on. And if the AC and
heat use 240 volts then monitor the voltage across the two hot input lines.
The power company's transformer may be OK, but 120 feet is sort of on
the long side for a residential feed, and if the original installers
skimped a bit on the feeder size that may well be where your problem
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.