Been reviewing electrical code in Canada, and can't find a definitive
answer to my question.
I have a ceiling combination fan/light fixture in my upstairs lobby
area. I want to know if I can split the hot in two and use 1 neutral?
My intent is to use the 1 circuit, branch to 2 light switches (fan /
light). The setup is already there and am wondering if I can just pull
an addittional hot.
That's the way it is usually done (in the US at least). Fan manufacturers make
double switches for just this purpose. We usually pull 3 conductor with ground
for the circuit. Another, simpler option is to put in a wireless remote. The
receiver goes in the fan itself and just needs one hot. The remote selects the
fan on/off, speeds, light, etc. No need for another hot to be pulled.
Justin West ( email@example.com) said...
Is there conduit between the light fixture box and the switch? If so, there
is likely plenty of room to pull another conductor.
I have done this once. It was in a highrise apartment, so conduit was in
place. The run to the switch was a "switch loop", which means no neutral
ran to the switch: just a live hot to the switch and a switched hot back
to the light. Replacing the light with a fan/light, an additional switched
hot was pulled and provided the switched power for the fan. The switch
was replaced with a double switch that fits in a single location.
If you don't have conduit to pull through, you can't just pull a conductor
on its own. If it is possible to pull a new Romex cable, then you can pull
a 14/3 cable to replace the existing 14/2. The three conductors in the
14/3 all become hot: one is always live, one is light switched, and the
other is fan switched. The white should be marked somehow (I usually use
a black or blue permanent marker to colour an inch or two at the end).
"Never ascribe to malice what can equally be explained by incompetence."
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.