A few days ago I wrote about the problem with 134V at the outlet. I thought it might be the ground so I added a couple 8' rods, but that was not it. I looked up at the power pole, and there I could see the neutral conductor was completely broken off! I called Southern California Edison and they sent a guy out within an hour. All fixed by the power company! Shared neutral outlet pairs now read 118V/123V. The neighbor's bamboo trees sway against the power wires when it gets windy.