This is a multi-part message in MIME format.
Content-Type: text/plain; charset=ISO-8859-1; format=flowed
I think the problem is that you can't answer a simple question, which
is, should I connect R and C to the block, or the terminal strip? Both
have screws to accept wire connections.
There's a level of confidence one gets after they've done something once
or twice (successfully). It's a bit unnerving not having the display
light up, and I can see that there's no return to the common side of the
transformer, so perhaps if I hook up the black wire to C I'll be in
business - at which point I'll probably have a question re: how to adapt
the multi-stage operation to a single-stage furnace.
Thinking about it, though, I guess W-R has tapped off C and R to the
block to power off-board devices.
I work with electronic technicians all day long (alarm systems), but
when I asked one of the senior guys if he knew anything about
heating/cooling systems his answer was "my furnace has a red wire and a
Questions from someone not "in the biz", may seem dumb, but you've
probably heard that there's no such thing as a dumb question, only...
<div><font face="Verdana">I have White-Rogers</font>
1F95-371 multi-stage thermostat that I'd like to try and use with my
plain vanilla residential furnace (Lennox).<br>
<font color="#ff0000" face="Arial" size="2">its a Lummox
with a WR stat</font><br>
- I only need it to control heat (W), fan (G) and AC (Y)<br>
- The R and C terminals on the unit have red and black wires
(respectively) soldered to a block which has 3 terminals on it (see <font
- If I connect W/G/Y plus the R wire, the display does not light up -
presumably because it needs a full-time connection to T (transformer
Has anyone wired up one of these successfully and can I adapt it to my
<div><font face="Verdana"><font color="#ff0000" face="Arial"
size="2">Yup, lots of times</font></font></div>
Please don't top post. It's annoying. And that 'stat looks like it is
for multi-stage specific application. Installer option does not show
anything for single stage operation. I could be wrong.
Tony, EE class of '66
Retired from Honeywell in '96
So how many control board have you fixed? That is my hobby.
Not a difficult task knowing how it works and with proper tools;
DVM of course, 'scope and IC tracker.
In the product description nowhere it mentioned anything for single
I don't have a problem with troubleshooting boards at the componant level. I
am still operating some of the HAM radio equipment that I designed and built
from scratch over the last 30 years. A thermostat is still nothing more than
a switch. A multi stage stat works just fine with single stage equipment.
All I carry on my truck are multi stage stats so I can configure them for
*ANY* application. Like I said before, you just have to be smarter than a
temperature controlled, ON/OFF SWITCH
So what is your call sign? Mine is VE6CGX with digital endorsement.
(Equivalent U.S. Extra class) It is not a matter of being smart, it is
matter of being logical. Remember IBM's motto? "Think"
Lately I am into fixing tube guitar amps for friends and neighbors.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.