I was just looking up some oddball outlet I got in a pail of
electrical stuff at an auction. I went to this website.
What I have is the # 24-15R
Listed for 347V AC.
Now I know what it is, but where do they use 347V AC ?
Or, for that matter, where do they use 277V AC which is also listed?
120 240 208 480 are all common, but these 277 and 347 I never heard
By the way, this is a very handy website. Bookmark it !!!!
If you have a 480 volt 3 phase circuit connected in the Y configuration, the
center of the Y (which is often grounded and also the neutral) to one of the
ends will be 277 volts. This is often used for lighting in buildings that
have 480 volt 3 phase power.
The 347 volts is the same way for a 600 volt Y connected circuit.
277 is the phase to neutral voltage of a 3 phase 480 volt system. Very
commonly used for the lighting in commercial buildings.
347 is the phase to neutral voltage of a 3 phase 600 volt system.
Phase to neutral voltages can be calculated by dividing the phase to phase
voltage by the square root of 3.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.