Found the problem. The neutral wire must have had a bad connection at
the circuit breaker panel because the last 3 or so inches of the wire
was fried. An electrician repaired it and everything is fine now.
Thanks for everyone's help.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.