Hi all, I am trying to wire a new light switch but the back to the
switch has 3 possible spots to put wires and I only have two wires from
the light. They are labelled, 1 2 and loop. Anyone who may be able to
shed some light on this??
On 1 Apr 2006 00:04:46 -0800, email@example.com wrote:
Unless one of those 'spots to put wires' is a green screw for a ground
wire, you might have a three-way switch, and you seem to only need a
I would highly recommend you get in contact with a peson more familiar
with switch replacement. Just to be safe. :)
tom @ www.NoCostAds.com
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.