firstname.lastname@example.org (Randd01) wrote in message
I was putting more than one light in the run of 14/3 wire. What I
should have done was wire one light in the 14/3 between the two
switches and then use pigtails to wire the rest of the lights off the
In hindsight it seems obvious. I think my problem was two fold. One, I
tend to not think too much when wiring 3-way switches. I follow the
diagram and don't really think of the logic. Two, it was the end of a
long day running wire underneath the house. Pulling wire while
crawling around in the dirt under the house is exhausting work.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.