I have a walkin closet that is approx. 10ft by 4ft and am adding a
light to it. When you walk in the closet you make an imediate left. On
the right is the shelving and on the left is a wall running down the
10ft. I am adding the light in the middle of the closet not above the
door. I know the code is 12" away from the shelves for incandecent and
6" away for fluorescent. My question is how far from the wall on the
left do I have to be?
Actually, the Code defines closet "storage space" as being 12" out from the
walls, or the width of the shelves, whichever is *greater* [that's more than 6
feet from the floor; below 6 feet, it's 24"] -- and requires the fixture to be
12" or 6" outside that space, depending on whether it's incandescent or
[Note that this is *not* a complete definition of storage space. Consult the
Code, Article 410.8, for the full definition.]
6" outside the storage space envelope for fluorescent, or 12" for
incandescent. Assuming there are no shelves on that wall, that means 18" or
24" from the wall.
Doug Miller (alphageek at milmac dot com)
So is a ceramic socket with a twisty flourescent bulb in it
an incadescant fixture, or a flourescent one?
And does code govern low-voltage flexible electroluminescent
tape like this stuff
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.