The circuits that share the 12/3 cable neutral are on different hot legs.
These are single pole slim breakers - that may be what is confusing. I
should replace them with double-pole breakers, then it would make more
Or am I understanding your suggestion incorrectly?
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.