My pump is in the return limb of the system. My vent pipe is in the
flow limb. When the pump runs in setting 2 air is sucked in through the
vent pipe. When the pump is on speed 1 this doesnt happen but some rads
remain cold. The cold feed is in the return limb on the boiler side of
the pump. Has anyone advice please?