OK, please bare with as I really don't know how to descibe
this properly. Both the old and new have 6 hole (connectors).
The current 2G2W Double Switch had 3 sets of 1 top and 1
The new one from TLC is a 2G2W Double Switch has 2 sets
of 2 top and 1 bottom connection.
The left switch is fine, but the right one needs to activate 2
separate lights. From what I can tell is that I think the old way
used a return path [the middle set]. There are 4 wires (plus
the earth), and from memory it's a red, black, blue and yellow,
but there seems to be only 3 connectors.
Does anyone understand what I am on about and if so can
anyone advise on wiring this up correctly?
There will be 3 holes per switch on both types. There will be a common for
each and two outputs for each. You need to identify which holes were which
on each switch and move the wires over.
Frequently, the holes will be labelled 'C' for common and 'L1' and 'L2' for
A two-way switch circuit where two switches in different locations switch
one or more lamps will commonly have 5 wires at one switch, and three at
the other. I've included the circuit below.
C 0==========================O C
0======================0============= Switch return
The three wires between the two switches might well be red, yellow and
blue, and there *should* be a further red and black at one of the
switches which goes to the light fitting as in a normal one way switch.
However, for some reason best known to themselves, some electricians will
feed the circuit from one switch and take the switched output from the
other. Or used a shared feed to the one way and two way switch on the same
*I don't suffer from insanity -- I'm a carrier
Dave Plowman firstname.lastname@example.org London SW 12
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.