# Balancing Radiators - New Method?

should be balanced to achieve an 11C temp drop may not be correct?
It's stated that as long as the same temp drop exists across all rads
then this is fine, whether it be 2C or 11C.
I had always assumed that the 11C drop value was based on maximising
boiler efficiency and/or most efficient transfer of heat from the rads
to the environment but now I'm totally confused.
Could someone kindly post a big dummy's explanation for me. TIA
In article , Bovvered? writes:
Yes, but for a conventional boiler the effect is tiny. If the return is 10C hotter than ideal, the flue gasses would be, say, 10C hotter (which is optimistic), so if we assumed a burner temperature of 1000C dropping to a flue temperature of 150C instead of 140C, that's only a 1% difference in boiler efficiency.
If the temperature drop is low, you might be running the pump faster than is necessary, although the heat from that adds to the house anyway.
Well you'd have to define what you mean by the efficiency of a radiator. Having a smaller drop at the same flow temperaturte would cause the radiator to give off more power as it's average temperature would be higher.
For a condensing boiler, the drop is more important, not for the sake of the drop itself, but to keep the return temperature down to give the efficiency benefits one hopes to achieve from condensing operation, whilst having the flow temperature high enough to give a reasonable average radiator temperature. 70/50 is a common design critera. Mine runs mostly at 45/41 which is a tiny drop for a condensing boiler, but because the return temperature is lower than the 70/50 case, I'm running more efficiently.
On 09 Jan 2008 23:12:00 GMT, snipped-for-privacy@cucumber.demon.co.uk (Andrew
So given that I have a non condensing boiler, the consistency of drop across all radiators is more important than the absolute values?
In article , Bovvered? writes: > > So given that I have a non condensing boiler, the consistency of drop > across all radiators is more important than the absolute values? Yes.
In an earlier contribution to this discussion,
Yes. And also remember that the whole point of balancing is to make sure that some rads are not hogging all the flow and starving the others - so if *all* your rads have a low drop, they obviously all have adequate flow.
Your drops *are* very low low though (assuming you're measuring them properly). I think I would be inclined to reduce the pump speed if its not already on its lowest setting.
In message , Roger Mills writes
Bovvered hasn't post his temperature drops so I guess you're referring to mine. The pump here has been set speed 3 until now so I've just reduced it to 2. I'll see about measuring the temp' drops again in a few days.
In an earlier contribution to this discussion,
Yes, I guess I am - if you were the one with 1 and 2 degree drops.

• We need a new boiler fitted in a one bedroom flat in London. There's currently a...
• next in

## UK Do-It-Yourself

• Since moving into our new house, which is 350 years old, we've been aware of...
• previous in

## UK Do-It-Yourself

• in message: A wire is taken from the switched live at the hall switch to both...
• last updated in

## UK Do-It-Yourself

• last posted in

## UK Do-It-Yourself

• We've had a little cold snap here in Maryland, just northeast of Baltimore....
• site's last updated in

## Fruit and Vegetable Gardening

• Charles Barkley: ?We Need to Stop the Defund or Abolish Police Crap? ?We need to...