Not wanting to engage in this debate because its over my head.
But, I can add:
I was moving a receptacle.
The wiring in the fuse box is "split" on two 15amp fuses red on left fuse,
black on the right.
I think you are right about meeting current codes. If you do repair
or installion of equipment, unless the code allows for certain
existing conditions, i believe you need to do work to today's
Curious, do you have a section? I understand you might be referencing
Canada's regs, so I just want to know the basis.
I mean, a whole house's disconnect can be six seperate breakers, so
why a receptacle is required to be one?
Thank you for your help,
tom @ www.ChopURL.com
Aw, I disagree. It's got:
Intrigue (how the hell do I do this)
Drama (did I do it right)
Action (I'm doing it)
Suspense (will it work)
Fear (where is the smoke coming from)
Comedy (ZAP! uh, guess I should have turned off the breaker)
I think electricity is the most dabblistic of em all.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.