A problem with a fluorescent fixture.--
At the end of four 48” there is a 24” fixture that I (a novice) have a
problem with. I replaced the 24” with a new fixture because the old one
didn’t work. Now the new one will sometimes light when turning on the
switch and if it doesn’t all I have to do is place my hand one or two
inches from the bulb and it goes on. It sounds like black magic to me
but I’m hoping that someone can explain to me why it happens and what I
can do about it. TIA
It would appear the fixture is not properly grounded. Your description
was very good, in that you said all the magic things. Make sure the metal
part of the fixture is truly grounded to the electrical ground (not neutral)
and all should be right with the world.
Most likely the fixture is not grounded. Another, less likely possible
explanation is hot-neutral reverse. These things affect electric field
distribution within a bulb that is trying to start.
Other less likely possibilities - try cleaning the bulbs, make sure the
ballast label says it is compatible with your bulbs, make sure the ballast
is wired properly.
If the fixture has a starter and you tried everything else, try
replacing the starter - preferably with one of a different brand.
Some cranky starters need light (photoelectric effect) to start. After
that, try a different brand of bulbs, preferably of the "Big 3" brands -
Sylvania, Philips or GE.
- Don Klipstein ( firstname.lastname@example.org, http://www.misty.com/~don/ltrouble.html )
I'd like to thank the responders to the below message. At least now I
know there's no "black magic" involved. My question (remember, I said I
was a "novice") is how do I go about "grounding" the fixture.
If you are not comfortable with this stuff, do hire a professional to do
The fixture should have three wires coming to it. One white, one black
(or red) and one green or bare copper. That green/copper wire should be
firmly secured to the metal parts of the fixture. There is likely a green
screw on the fixture where the wires come in to secure the ground to.
Thanks Joe for the info. I checked and found that there is no 3rd wire
from the last 48" fixture. Maybe that's why the original 24" didn't
work? I'm just going to leave it alone until I can get a pro to look at
it. Thanks again.
Joseph Meehan wrote:
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.