Electrical subpanel- wire directly to meter?

You would have to check your local codes, but we have three separate service entrances (main panels).
Our electrical meter is located on a pole out at the road. Then the power comes down to a junction box behind our pump house. Separate lines then run to individual service entrances at the pump house, garage, and our house. Each building has it's own main breaker, grounding electrodes, etc. Completely seperate and isolated from each other (other than the incoming power).
We built the pump house first, then our garage, and finally the house. So we wouldn't have been able to run a subpanel off the house anyway.
However, I did run a small 30A circuit off the house panel to a small subpanel in our storage shed.
Anthony
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

So how are the service entrance conductors sized? If the ampacity of the service conductors is less than the sum of the ratings of the main breakers on the three main panels, then the only thing protecting the service conductors from overcurrent is the statistical unlikelihood of all three services drawing maximum power simultaneously?
Thanks, Wayne
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
The NEC doesn't require the main service conductors to be equal or greater than the sum of the up to six main disconnects. It does however require the calculated load to be less than the size of the service conductors
wrote:

<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

So nothing protects the service conductors from overcurrent. This surprises me, but I guess if the main service conductors overheated due to overcurrent, they are far less likely to start a fire in an enclosed space compared to a branch circuit or feeder. I suppose that is also the the reason that the distance the service conductors can travel within a building before the main disconnect is restricted.
Cheers, Wayne
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
It's surprising to me as well. Usually the NEC seems to overprotect wiring and equipment. Every time I, as an electrical contractor need to add a load to one of these types of services, I have to do a load calculation, just to be sure that the homeowners and electricians before me, didn't overload the mains
wrote:

<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
Wayne,

I installed a 200A panel in our garage, and another 200A panel in our house. Each panel is supplied with three 4/0 aluminum conductors that connect to the power companies junction box. Our pump house only has two breakers, 20A for the pump, and 15A for the lights. It has been many years since I hooked that up, but I think I used three 1/0 copper conductors for that panel.
The cable between the junction boxes and the transformer at the road was provided and installed by the power company. I wasn't here when they hooked us up, so I don't know what kind of cable they have on their side. When we hooked up our house, I asked the power guy about the cable, and he made a comment that their cable was a little undersized to be powering all three buildings. But he said that was done routinely a few years ago before they started running load calculations. He said it wasn't a big problem, since we were unlikely to max out all panels at once, but we may notice dimming lights if I was powering up equipment in the garage while the heaters were running in the house or something.
But, in the 15 years or so we have lived here, I've never noticed any problems with dimming lights, or any other signs of too much current draw.
Anthony
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>
Wayne Whitney wrote:

They are sized by the load calculation adding any allowance desired for future changes.
--
Tom Horne

"This alternating current stuff is just a fad. It is much too dangerous
<% if( /^image/.test(type) ){ %>
<% } %>
<%-name%>

Site Timeline

• Kitchen faucet chatter

• - next thread in Home Repair
• Wall tiles on floor?

• - previous thread in Home Repair

• Ring doorbell

• - last updated thread in Home Repair
• Share To

HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here. All logos and trade names are the property of their respective owners.