I have a 1924 house with knob & tube wiring in some places. I am
having trouble following the single knob & tube wire in my attic after
it leaves the ceiling light. It seems to disappear into the attic
floor boards 2 feet before it reaches the edge where the top of the
wall of the room would be. How do I find this wire? Is there anyway to
replace it with romex? Even if I tear out the bedroom wall and rewire
from the light switch up to the attic , how do I get the romex into
the attic if it has to go through a very thick joist? Must I destroy
the ceiling as well? I guess they used to run the knob & tube directly
in the plaster?
They were relatively paranoid about electricity during K&T days, and I
_highly_ doubt that it's buried in the plaster.
If the wiring is in good shape (most K&T still is), I wouldn't just replace
it for the sake of replacing it. Most inspectors I've spoken to tell
you not to bother unless you're doing major rewiring and have to take
the plaster off anyway.
If the section is in tubes, you can sometimes pull it, but the remaining
holes (especially if the tubes don't come out) will probably not be big
enough for romex.
There are some electrical wiring detectors on the market, much like the
electronic stud finders. Not _too_ pricy. But not entirely cheap either.
Chris Lewis, Una confibula non set est
It's not just anyone who gets a Starship Cruiser class named after them.
firstname.lastname@example.org (margaret flaherty) wrote in message
If there are knobs holding on to the wire in the wall you'll never
pull new romex by attaching it to the existing wire and pulling it
through. Just abandon the K&T in place and run new romex. You can
measure to make sure you're over the switch and drill a new hole from
the attic side. Drop the romex down and then run it to the ceiling
fixture. The K&T wire from the switch to the fixture can just be left
in place. You can also run power to the switch down through the wall
in the same fashion or dril a hole from under the house and then use a
fish line to get it to the switch. I just rewired my whole house this
way. There is no need to rip out a lot of plaster.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.