Is it normal to have some air coming in from the fan into the
bathroom. I have a screen at the end of the exhaust pipe and there is
a flapper damper at the fan itself, factory installed. I cant really
use a sophet vent because it restricts the air flow and causes a
whistling sound when running. There was still air coming in that way
too, but not as much. Had to be windier. Thanks!
I believe you will find that most fans do have some back draft. The
good ones have less. The installation and the air pressure inside the home
will also make a difference. Your home needs some air exchange. For
example when your fan is on, air has to be coming in from somewhere to
On Oct 11, 12:43 am, email@example.com wrote:
It's not unusual, unfortunately. A couple of reasons. The spring
loaded damper at the outlet is a cheap piece and loses its seal. The
vent pipe is also a thermal short circuit to the outside air. They're
usually run through unheated spaces and consequently the air inside
loses its heat and the cold air looks for a lower spot to go lie
down. Namely, your bathroom.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.