Can standard baseboard heaters be placed onto a 30A circuit provided I use 10 AWG Cu wire? Or is there some requirement that they only be placed onto a 15/20A circuit? If I do place them onto a 30A circuit can I make 12 AWG taps to individual heaters provided that the taps are less than 50 ft? Can a "tap" come directly from the breaker box?
Thanks again, William