Can standard baseboard heaters be placed onto a 30A circuit provided I
use 10 AWG Cu wire? Or is there some requirement that they only be
placed onto a 15/20A circuit? If I do place them onto a 30A circuit
can I make 12 AWG taps to individual heaters provided that the taps are
less than 50 ft? Can a "tap" come directly from the breaker box?
On 10 Sep 2006 07:44:03 -0700, " email@example.com"
I have a Square D breaker right here. The clamp where you attach the
load wire has places to connect 2 wires There's some markings on the
side that show 2 wires for 14 to 10 gauge, but only 1 for 8 gauge.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.