On Wed, 23 May 2007 07:19:24 -0400, "RBM" <rbm2(remove
He should first measure the voltage between hot and ground or he may
burn out his continuity tester, and may knock himself off the ladder
when the thing gives a big spark.
Unless he is positive he knows which wire is supposed to be the
neutral, he should also have tested for voltage between the "neutral"
and ground also before he used a continuity tester between the two.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.