There are 12 photos here
showing a genset that has failed twice the same way after only several
dozen hours of running, most of that just to start it periodically
each week to make sure it's working. In the photos there is a round
gray generator/alternator and you can see the end cap on it. If you
look at the small round holes in the end cap you see that the screws
that hold it to the frame don't seem to be there. You can see the
broken screws (look like Allen head to me) laying on the baseplate. As
far as I can tell this end cap holds the end bearing for the common
centershaft that goes thru the middle of the generator/alternator and
is direct coupled to the propane powered engine that powers it. These
small screws have sheared like this twice now. The only reason I can
think of is that the bearing in the end cap seized. It's my sister and
brother in laws backup generator and the company didn't really want to
fix it under warranty the first time, trying to claim "abuse" and is
less thrilled about it going out a second time. The company claims
they have never seen this happen before, much less twice on the same
Thoughts on why it failed????
Speculation on my part, but I doubt abuse has anything to do with it.
I'd think some sort of misalignment of the bearing and/or shaft. Under
normal running or even constant full speed operation, bolts don't
break unless stressed beyond capability and intended use. A very
small but constant whipping of the end shaft due to misalignment can
cause bolts to break from the stress. I'm talking thousandths of an
inch, not even visible, but at 3000 rpm, it is a bit problem.
Rather than try to weasel out of the fix, the manufacturer should be
doing more investigation.
Agree with above.
Or they have got a batch of faulty bolts.
Or the rotating bit is out of balance.
But in any event not the fault of the user.
In the UK they could legally demand money back/new generator as the
generator was not fit for purpose.
When I was installing and servicing a lot of Generac units, I had the
phone number of the vice president of the company who was in charge of
service. Whenever some strange thing like that came up, the boss was
very interested in finding out what was up so it didn't happen on a
lager scale. I would see if I could get hold of someone up the company
ladder about the problem you're having since it's possible a defect got
past Quality Control or the unit may have been damaged by mishandling
somewhere down the line and you have a bent shaft. o_O
What does this end cap do? Looks like just a cover. Is there a gasket
between the end cap and the gen.? Is vibration excessive when you run the
gen.? Have you run the gen. for an extended period (several hours)?
On Thu, 4 Apr 2013 08:35:21 -0400, "David L. Martel"
All I know at this point is what I've seen in the pictures, it's not
my genset, it's my sisters back east. The last time I was there the
electric was out and the genset ran for about 12 hours and seemed
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.