...great ugly coil of earth wire and associated clamps bonding an
outside tap supply pipe to the overflow pipe from a lavatory
cistern? I ask because it just looks so awful in what is
otherwise a tidy room. As the cistern overflow pipe is only
attached to a china cistern and runs almost immediately back
through the wall there seems little chance of it causing a
problem. I suppose I could replace the current copper overflow
pipe with a plastic one which certainly won't need earth bonding.
My brother had his house re-wired about 2 or 3 years ago and had loads of
earth bonding ugly cables put in all over the place to meet with 'current'
regs. This month he's having the bathroom renovated with a walk in shower to
replace his bath, a new toilet fitted etc and they've told him that earth
bonding has gone out the window since more and more people are now using
plastic for their water pipes. He'd have saved a nice chuck of money if he'd
had the house re-wired now and he wouldn't have loads of cable and brackets
sticking out all over the place.
I suspect that you are mistaking the differences between the 17th edition
regs and the 16th edition regs and also forgetting the fact that Muddymike
is not working in a bathroom or shower room :-)
You do not need to supplementary bond in rooms that are not bathrooms or
shower rooms. You can remove the cable from the overflow and you are safe.
One small problem may be that you have a rising metal water supply entering
the building. It is possible may this may have to be bonded to your CU.
I have never understood what a pipe like this is liable to
conduct. It is 18 or less inches long, connects to a cistern via
a plastic connector one end, hangs in fresh air the other end and
is mostly buried in a wall. Whilst on the subject. Why are
bonding earth cables mostly ten times longer than they need be
and wound into a fancy coil?
Is it lightening strike the bonding protects me from :-)
Sorry. The overflow pipe is not the problem, it need not be bonded at all in
I was refering to the incoming water supply to the toilet when I mentioned
You can remove the unsightly, over long and unnecessary cable.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.