I would like to clean the ducts in my house (1966 ranch; 1400 sq ft
main level - floor registers, 1200 sq ft basement - ceiling registers;
Denver metro.) Nothing _terribly_ wrong with the air flow, but a couple
of the registers are producing mediocre air flow, so I just want to
make sure and do some duct cleaning.
I should add that this is not an issue of anyone in the house suffering
from allergies or anything like that. Just trying to improve the air
flow to make the whole heating/cooling system more efficient.
I've read several threads on this discussion group, and it sound like I
should avoid duct cleaning services, which usually are not worth the
price they are charging. So I'm thinking of getting a shop vac and
cleaning the ducts myself - just push in the shop vac hose as deep as I
can and try to vacuum all the junk.
I'm pretty new to this, so is there a specific shop-vas
type/model/brand that you would recommend for this type of job?
Note: the narrowest vent openings are 1 3/8 - 1.5 in.
I'll appreciate any helpful pointers.
No flames/sarcasm, please :)
It would take huge amounts of debris to noticeably affect air flow,
so that's probably NOT what's going on. If you really have sub-standard
airflow, it's more likely that a duct has collapsed as a result of
something falling on it in the attic (e.g.). Or perhaps your furnace
fan is now only operating on low speed or is binding.
If you want to clean the ducts on general principles your best bet is
probably to forget about the shop vac and instead go to Harbor Freight
and get one of their $3 +/- dryer vent brushes and swish it around in
the ducts while the furnace fan is running.
Everything I've read indicates the commercial duct cleaners are mostly
purveyors of snake oil.
The e-mail address in our reply-to line is reversed in an attempt to
minimize spam. Our true address is of the form firstname.lastname@example.org.
Those are possibilities, but more likely it's just a function of system
balance. At full damper opening, all the various outlets likely vastly
exceed the CFM rating of the furnace blower. With the registers all open
the airflow is going to vary at each register based on the restrictions
on it's particular run, i.e. twists and turns. By reducing the damper
setting on registers close to the furnace you provide more air to the
further out registers.
An HVAC tech would balance the system by checking the CFM spec on the
furnace, dividing that by the number of registers and then using a CFM
bal-o-meter to measure the output at each register adjusting each
several times until they are all flowing correctly.
Of course when you close off heat to a room you don't use in the winter
or A/C to a room you don't use in the summer it throws things out of
balance and since nobody thinks to mark the original damper position, in
a year or two the system is hopelessly out of balance.
Bad idea since that will blow everything you knock loose out into the
I wouldn't go that far. Duct cleaning is certainly something that should
be done as no furnace filter will trap everything and there will be crud
buildup. I think the issue is that some duct cleaning services for the
residential market don't do a very good job and sometimes have marketing
that exaggerates a bit.
Not the guys I had do my last house. They stuck a pneumatic air hose in the
vents with some kind of rotating head on it with some spaghetti-like rubber
bristles about 6-8" long, and put a vacuum thing on the furnace-end of the
system. The air hose thing beat the dust loose and the vacuum pulled it out.
I had it done only because the hardwood floors had recently been refinished,
incl. sanding to bare wood. It had probably never been done before either,
40 year old house.
As another poster said though, your problem probably isn't the dust. It's
either a physical obstruction in a branch supply (or return), or the
furnace's blower is going bad, or some other issue.
If previous owners had animals etc, the return ducks
are the problem.
The house I purchased NEVER had the ducts cleaned before. (50 years)
When I swtiched from oil to gas heating replacing the original furnace
I had the duct profesionally cleaned.
WOW, there was LOTS of crud on the return ducts.
(each room in my house has a return duct and a heating duct)
The heating registers werent too bad, mainly because the crappy
old filtering systems did do somewhat of a good job in its years
of use. The intakes though had dog hair, baseball cards, monopoly
money... All fun things in them.
For the 250.00 I spent I feel I got my moneys worth out of them.
They were there for 4 hours cleaning out the system.
Now that they systems been cleaned, I would LOVE to get some sort
of filters to trap crap from getting into the intake registers...
Can this be a DIY job???? Humm maybe. Thats if you can get into the
ductwork easily with a decent brush or something. To get the stuff
out of the system they cut a hole by the furnace ducts and attached a
bigass hose from a truck to my furnace. Can you create that kind of
suction needed??? Maybe but not with a standard shopvac.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.