Just moved into a new house (about 4 years old). The central heating has a
1. Should the pump make much noise. When the heating is on we can here the
pump going in the living room!
2. After the heating turns off at 2130, during the night we can here the
pump start up again, and after a while the all the radiators are warm, the
timing is definatly not set to come on. Is there anything else that would
cause the heating to come on??
You don't say where the pump is. There are several possibilities
a) The pump is set unnecessarily high. Try turning it down using the
small control on its terminal block. Check that all the radiators
still heat up OK afterwards and that the boiler is not tending to fire
for short periods - less than a minute.
b) The mounting arrangement isn't good and it is setting up some kind
of resonance in the pipework. Some pipe clips may help, or may not.
c) The pipes are clipped but to a stud wall and it is acting as a
d) The pump is a cheap contract grade one and is on its way out. This
is entirely possible if corrosion inhibitor wasn't used in the system
and sludgy water is circulating. With some pumps (e.g. types that
used to be fitted as spares by BG) it's possible anyway.
A frost thermostat in the boiler or somewhere else. Where is the
boiler? If it's in a garage or something, then this could explain
it. Even indoors, if the frost thermostat is set too high, the
heating will come on unnecessarily. Generally setting it to 8 -10
degrees is reasonable.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.