On Mon, 16 May 2016 15:09:29 -0400, firstname.lastname@example.org wrote:
I was told this about not using teflon tape back in the late 70's or
early 80's. What I heard was pretty vague, and I dont recall who said it
anymore. Anyhow, these days we have better access to information. Either
way, I guess I was told correctly to NOT use it, but for the wrong
reason. What you said makes a lot of sense. I am fully aware of using
teflon tape on plumbing, and when I'd first turn on the water, the
faucet strainers would clog. I'd remove them, and find rust particles
(if ther was OLD steel pipe involved), -AND- pieces of teflon tape,
along with little bits of solder (on copper pipe). On plbg its easy to
remove, but I could see orfices and stuff getting quickly clogged on gas
I'll just stick with using pipe dope on all gas pipes!
Thickness yes, not any different otherwise (barring the color, of
course). White PTFE is single thickness, yellow is double and pink is
I know of nowhere it is in any Code requirement and unless it's been
changed which I think it hasn't, the National Fuel Gas Code handbook
2.6.7(d) refers to using pipe dope suitable for use with gas and says:
"This requirements does not prohibit the use of teflon tape as a pipe
dope. [Further comments regarding workmanship elided for brevity]"
The requirement for the thicker tape (hence yellow as common identifier)
is the only one I'm aware of.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.