That requirement is for killing all the service conductors to a
building, so it applies at the main disconnect. It doesn't apply for
subpanels. It would apply for a feeder to a detached garage, which
could terminate in a MLO panel as long as there are 6 or fewer
breakers in it.
two things around here ALL basement outlets must be GFCI protected.
had big hassle with two different buyers at home sale time, I upgraded
with basement space install some ingress egress windows which will not
only add light and air but qualify the added space as bedrooms, very
valuable when its time to sell!
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.