I just bought a older home is a Juccuzi submersible well pump. About 2
weeks ago the capacitor went bad. I installed a new one no big deal
until this morning I woke up with out water again. I went and check the
capacitor and It was bad again. I have since replaced it twice today
and the pump runs for about 15 minutes and then blows the capacitor.
And ideas on what the problem is? Any help would be greatly great.
Assuming you are using the correct capacitor (high enough voltage,
etc), I have a feeling your pump motor is going bad.
However, before you pull the well (a big job), be sure there are no
worn or pinched wire where they enter the well (or anywhere else).
Wires can often get pinched at the well cap.
Sounds like the cap is "in circuit" all the time...
That would most likely mean the centrifugal start switch that opens up the
circuit and removes the cap from the circuit is not doing it's job....good
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.