Have a outlet in a bedroom where one side is live all the time, the other side
is switched from the wall. The original outlet went bad, when I removed it I
wired it the same way it came off. 2 wires on the top the 1 white wire on the
bottom(white). Problem now is that the both sides of the outlet are now live
all the time, the switch on the wall has no effect. Did I do something wrong?
or is there a special outlet I need to use for this type of installation?
Content-Type: Text/Plain; Charset=US-ASCII
Take the outlet back out and "break-off" the brass tab on the side.
You will then have what you re looking for.
Content-Type: Text/HTML; Charset=US-ASCII
<body bgcolor="#16181e" text="#7db392">
wires should be removed; isolates the hots. This "SHOULD" be the side with
the black wires/brass colored screws. Do not so this on the other tab.
Sites on the web *if you do the research* show this visually.
On 20 Dec 2004 01:48:05 GMT, email@example.com (DonLanger) wrote:
Split receptacle wiring requires removal of the metal break-off tab
located on the side of the housing in the middle. Twist it off using
a pair of pliers. There are actually two tabs, one hot and the other
neutral, so examine the original receptacle to see how to configure
your new receptacle.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.