This new house of my daughters is going to drive me crazy.
The cable wire is strapped to the SE cable (not a metal conduit), with
cable straps I thought NEC guidelines said this was a no-no. If I am
correct and you happen to know the chapter and verse, please refer to it.
If I am wrong, I should be right. This just looks like it's wrong. Before
I tell her to call the cable company, I want to make sure I am right.