I just moved into this new house one
year ago. I have noticed a musty smell
in the hot water. I've never noticed it
in the cold water. The water comes from
one of several wells which are shared by
several lots in the subdivision. There
are only 4 lots occupied in the
subdivision, so asking others probably
wouldn't help as they might even be on a
different well. And the smell is so
minute, I'd bet most people wouldn't
even notice. BTW the water heater is a
propane fired, direct through the wall
vent (PVC) unit. Should I put in a
filter? Or, any suggestions???? Thanks.
How much hot water do you use?
Water heaters are multiplying grounds for nasty things (which is why one
should never ingest hot water).
If you use only a small amount, try draining the water heater to fill it
with fresh. Find some way to inject a spoonfull of bleach into the
Good point, but if you don't ingest any of the water from the heater, you
should be (mostly) okay with a lower temperature. Meanwhile, a lower
temperature will reduce your fuel bill and, more importantly, save the earth
from natural resource depletion, global warming, and other assorted ills.
It's for the children.
I manage the wells/water system for what sounds like a very similar situation -
we have 28 lots drawing from 8 wells.
The first thing you need to do is find the person/company that manages your
well. What you didn't mention, but is highly likely with multiple houses drawing
from a common well is the storage tank. Depending on the design of the water
system, it's very likely that the storage tank is vented to the atmosphere. If
not treated regularly, the storage tank will develop algae over time. While
still drinkable, this leads to water with a musty odor, especially when heated.
The appropriate amount of chlorine will knock out the algae and take care of the
When you find the manager of the well, you can ask when they lasted tested the
water for contaminates. We do annual testing for nitrates/nitrites and Total
Coliform/eColi. The nitrate/nitrite testing catches any unwanted runoff from the
surface contaminating the well water. Total Coliform is harmless, but if it's
present, is an indicator that other bad things may be getting in the water (ie
If your funds are unlimited, there's lots of other tests you can buy, but these
are relatively inexpensive and cover the most common well problems.
Here are the results of my testing. The
smell is only from one faucet, a
bathroom vanity on a cultured marble
base. I went to the other bathroom with
the same sink and faucet, drew out hot
water, let is run down the drain and no
smell. We use this vanity very little.
Went back to the original smelly one,
and drew out a glass of hot water, took
it out of the room and smelled it ....
no smell. As someone mentioned, it is
the drain ... I feel stupid for not
seeing (aaaah, smelling?) it. I removed
the pop up stopper and it was grubby,
plus below it was pretty grubby also. I
will clean it with a bottle brush and
some bleach spray. That said, I will
check with the Home Owners' Association
on well testing. But, right now, as
there are only 4 lots occupied, and one
is the developer. The developer and his
dad, is pretty much the association for
Water heaters have a sacrificial anode inside to reduce electolysis when
dissimilar pipe fittings are used. This can deteriorate and cause a
sulphur-like smell and taste in the water. Iron reducing bacteria can do
this as well. My suggestion would be to replace the water heater, if the
one you have is old, or you suspect that it's the anode. Chlorination can
kill the iron reducing bacteria,
On 10/02/2010 04:03 PM, firstname.lastname@example.org wrote:
ITYM 120F, 140F hasn't been the recommended setting for decades
(although there are good arguments why it should be so; legionnaire's
disease combined with the prevalence of mixing valves being two. The
main argument *against* that I can think of would be the increased
delta-t between the inside of the tank and the air around it, but that
can be mitigated by better insulation.)
replace "roosters" with "cox" to reply.
the hotter the heaters output temperature the greater the scalding
risk., and higher costs to keep the hot water hot, plus my personal
opinion is that the hotter the bwater the shorter the heaters
for me i prefer cooler hot water.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.