It seems to me that when a bathroom fan is running with the door
closed, the makeup air comes primarily from the gap between the door
and the floor. Is there a formula or rule of thumb for the needed
area of this gap depending on the CFM of the fan?
I assume FPM is "feet per minute", and you are calculating this by
dividing the CFM of the fan by the square footage of the opening?
Right now I have a half bath with a 50 CFM fan, so I should have at
least 50/250 = 0.2 ft^2 of gap. With a 28" door, that's 1" of gap, so
my current 7/8" is marginal. In the full bath with a 80 CFM fan and a
28" door, I need to have 1.6" of gap at the bottom. Do these numbers
An FPM of 80 sounds crazy, since, for example, a 50 CFM fan would need
5/8 ft^2 of area, or a 3.2" gap beneath a 28" wide door.
You can stretch the velocity limit above 300 FPM.
For example at 400 FPM the velocity pressure is (400/4005)^2 =~ .01" water
The total loss (assuming a 0.5 entry coeff.) is .015 " water which will have
negligible affect on your fan capacity.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.