First, thanks to a few guys here in the group; over the last week
I have successfully mounted, installed, wired and tested a
Transfer Switch, including building the cable for the generator,
and passed inspection with only one gotcha: The inspector didn't
like the power strip I used for light while I was doing the
wiring - you know, the one that was plugged into the generator
for use while I had the house dark? - the first tap he checked
didn't have a neutral!
Irritated, I asked him what thay had to do with the job I was
paying him for and he admitted "nothing" and grabbed for his
So, it went without a hitch except for the poor sense of humor
the inspector had.
I'd name each of you but I'd screw up the names or leave one
out, so - you know who you are anyway.
In the process I also removed about a thousand feet of excess
bare wire inside the breaker box, allowing me to neaten it
considerably. Even found a couple loosened neutral screws.
Thanks again guys,
Click to see the full signature.