I have an A.O. Smith gas water heater with power vent. I'm the third
owner of this house and the water heater is probably original (13 years
old). I've noticed a couple of problems in the past few months. The
first problem is that about a month ago the pilot light went out twice
in a few days timeframe. I was able to re-light it, with a little
trouble getting it to stay on (I didn't do the one minute test of
holding down the pilot after I lit it to see if it stayed lit) and it
hasn't been a problem since. I guess the next time I'll try the test.
Anyway the main problem is that the burner is not kicking on when I run
out of hot water. To get it to come on I have to unplug/replug in the
blower for the vent. Obviously I have to remember to do this once
every day/few days. Is that a sign of a bad thermostat or could it be
something else? I have a home warranty with a $50 co-pay, but is this
something I should/could fix myself?
The Power Vent heaters must "prove" the draft inducer fan
is actually coming on before opening the Main gas valve.
I will go out on a limb and speculate that your heater is
failing at that point for one reason or another and then
locking out. Unplugging then resets the circuitry.
In short, it's more than a simple DIY homeowner problem
and you *may* be ahead to call the warranty folks .
The pilot problem is not likely a big issue, likely a thermocouple.
The other one is a bit more of a problem. Without the manual I don't
think I would try to fix it, especially since you are talking about a water
heater than is 13 years old.
It might be worth the $50 co-pay, especially if they take care of both
problems (about $10 for a thermocouple.) But I would not put any real money
into it at this point and any leak is likely to be the end of it.
Nice thing about a home warranty, if they decide it is not servicable, you
get a brand new one to replace it. Hopefully it is a part you can't
replace. In your case it may be a sensor or control module.
I got a brand new garage door opener because the gear box split open.
IMHO, worth the $50
yeah with such a old water tank its very likely to just be replaced,
since parts are likely scarce and disturbing the tank will likely
result in a leak. too bad it just didnt start dripping that would get
you a nice new one.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.