I bought a double pole switch for my router table. It says it can handle
20a/240v or 35a/120v.
Why would each pole be able to handle only 20a on 240v (with 120v on each
pole) but 35a on 120v? Or does it assume you are connecting the 120v to
both poles to get the greater capacity.
I wrote the company but got a reply that didn't really say anything.
My guess is the reason is if the poles start to open at very slightly
different times you will have a 240V arc across the pole that opens
earlier. A higher voltage arc is harder to extinguish.
For the same reason you can't reliably parallel the 2 poles for 120V. If
one pole opens slightly early the other pole will interrupt the full 35A.
AC only switches (not intended for DC use) intentionally operate slowly
so zero crossings of the AC supply voltage help extinguish the arc. Slow
operation probably makes it more likely the poles will open at slightly
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.