Can anyone tell me the maximum line-of-site distance that a breaker box
sited outside an A/C compressor can be from the A/C unit? I want to put a
breaker box about 15' from the unit (line-of-site), but I'm not quite sure
it is to code (Virginia).
I think I'm misunderstanding your question. If you want to know the maximum
distance an A/C disconnect can be from the condenser, that's something else.
It must be "in sight from" which means in sight of and within 50 feet.
The current box has about 12" in front of it. It was installed about 40
years ago before the code said that there needs to be 3' of cleared space in
front of it.
If I replaced the box near the compressor, there would be too many bends in
the wire to be to code. If I put it 15' away, there would be three bends
between the breaker box and the a/c, and 3 bends between the breaker box and
the electrical panel.
of bends, but this does not apply to romex.
If you do have conduit, you are allowed to put a box at the existing
location. The requirement is between pull points, not the breaker
box. This can be no more than 360 degrees.
Everything outside should be weatherproof.
HomeOwnersHub.com is a website for homeowners and building and maintenance pros. It is not affiliated with any of the manufacturers or service providers discussed here.
All logos and trade names are the property of their respective owners.